Solar Lighting Comparison Guide
Sizing and reporting solar powered lighting performance relies on historical databases and methods developed by various organizations over the past couple of decades and include a fair amount of judgment and experience supplied by the manufacturer. For this reason, it may be hard to compare offers.
A good way to help standardize is to start with the same assumptions for calculating performance. Your suppliers should be able provide you with their assumption values and rationale. If assumptions differ, select a reliable source and ask manufacturers to base their calculations on those assumptions. NREL and NASA both provide credible data, with more locations reported by NASA.
Alternatively, select the assumptions of one supplier as the benchmark for your specification. We suggest including the following values.
More light doesn’t always mean better light. If you don’t have a photometric comparison tool, like Photometrics Pro and time and resources allow, ask suppliers to provide a layout based on your drawings and lighting requirements.
Another means of comparison is a small “typical layout” showing the spacing required for your application for example a span of a 20’ wide roadway or maximum spacing between four parking lot lights. At the very least, observe differences in templates showing the same lamp height and measuring fc/lux at grade. Look for a wide/even distribution of light versus a high peak light level at the center of a narrow field.
Maximum Power Tracking Versus PWM
Maximum Power Tracking (MPT or MPPT) allows you to collect 20%-30% more energy than a PWM controller will for a given panel size. Energy collected with an MPT plus a 100W panel is greater than the energy collected with a PWM controller and the same panel.
Multi-Stage charging is required to use the full capacity of your batteries. Single-Stage Charge controllers will only charge 90% of your battery capacity.
Energy management functions track the state of charge of the battery and make adjustments to protect it when there is an anticipated energy shortage. SolarOne’s RTE (Run Time Extension) is adjustable to be aggressive or conservative. The default settings activates adjustments in less than average conditions.
A remote control can save time and money by allowing you to check and adjust your solar lighting system without opening the enclosure. This is saves money, especially when the enclosure is located near the top of the pole.
In most cases your lighting profile will remain unchanged, but you may need to make adjustments. Neighborhoods may request an earlier dimming profile or a “lights out” period; you may encounter unexpected shading or decide to use your lights in a different application. With flexible remote-control-programming, you can make the changes without electrical services, shipping or down-time.
Error Reporting And Diagnostics
Controllers that can report status and report error types make maintenance faster and easier.